Crestron Residential Lighting Design Guide
GreenLight OptionsCAEN Enclosures
All power feeds must be protected by 15 or 20
amp circuit breakers (supplied by others).
Use copper conductors only rated 75°C
All wiring must be installed in accordance with all local
and national electrical codes.
Two snap bushings are supplied. If required, insert into
knockouts at the bottom of the enclosure to prevent
damage to low voltage wiring.
Class 2 field wires must be kept separate. Refer to the
illustration showing singlewide and doublewide wiring
details. Areas for high voltage (Class 1) wiring are shown
along the top and side(s) of the unit. The lower area is
reserved for low voltage (Class 2) wiring.
Tighten all CLT-Series terminal block screws and
grounding terminal block screws to the torque specified
in the Torque Data table.
Failure to properly tighten the screws may
result in poor electrical connection and overheating of the
Wire Range &
22 - 10
14 - 10
6 - 4
Torque Data CLT Terminal Blocks Grounding Terminal Blocks Wire Range 22 - 10 14 - 10 8 6 - 4 Torque (In-Lbs) 9 35 40 45